It might be a good idea to get several bids and look each over for the details. Whatever you do, when installing feeders from the meter base to the panel, do it properly by contacting the power company to disconnect your service. Better to be safe than sorry. If your heated pool is electrically heated, I suspect you might need that much. Triplex is an free air rated cable and is not to be put into conduit. In most cases when installing an electrical panel, the power company will not connect or reconnect power to your new panel unless it has been approved by a local electrical inspector. The streamlined way I'll start with the streamlined approach, since even with a bit of plan review and explanation, it's still going to be cheaper and easier most likely than the subpanel approach in your case.
Includes planning, equipment and material acquisition, area preparation and protection, setup and cleanup. Running ether through the conduit or through a hole conduit looks much better and hook up the same way in the meeter box. This method uses job specific detail for superior pricing accuracy and transparency - and has become an industry standard through publications and guidance of leading trade associations, including: , the , the , the , and the. Check for proper sizing of service entrance conductors. What you are proposing to do is bring this into your house. This is because the primary fuse has not blown and disconnected the power. Any given project might be priced on a per item basis, or the electrician might simply craft a bid based on the number of tasks to be performed.
Make sure to leave your self excess wire always. Please be safe and coordinate your panel installation with the local building authority and power company. I did an online load calculation of my appliances and it appears I could pull up to 125 amps. Electricity enters the home via the meter socket and service-entrance wire. Less wire, less pulling, less hassle. I sure hope this doesn't make you want to kick me in the butt, but, what if I relocated my incoming service wire to go directly to the inside panel and then use the outside panel as a sub panel? I'm wondering why he wants to remove your existing 200 amp panel, and replace it with another 200 amp panel. This is normal as you never uses every circuit to its maximum rating at the same time.
Frequently, a homeowner will purchase a property with an outdated circuit panel, such as one with only 20 to 40 amps. Obviously that was not the case. Is there something wrong with the existing panel? Electrical Service Panel Cost Non-discounted retail pricing for: 100A primary electrical load center. When this main breaker is on, electricity flows to the bus bar of the main breaker panel and is allowed to flow through each branch circuit breaker to individual branch circuits. Otherwise, 200 amps will support a lot of house. Install breakers and test circuits.
However, you must change the main disconnect breaker to a 100 amp disconnect. Note make sure to use a ground rod clamp to secure wire on each one make sure you put them on when you start to run the wire when you run the wire back through to the first rod makes sure you go back through the ground rod clamp tap clamps on with hammer. Come to find out the rules changed or the original planner had it all wrong. I originally was going to have 2 200 amp panels put in as the planner for the electrical company came out suggested that a year ago when I was having the location upgraded. The house is 1200 sq. There may be good reasons why the guy is suggesting replacing the panel and going to 400 amp service.
Just so you know that on a 100A service panel you could have a number of breakers that when you add the ratings for each breaker it adds up to more than 100Amps. This is typically done in commercial applications using what are known as feed-through lugs in commercial panelboards to feed a second panelboard directly from the busbars of the first without any intervening switch, fuse, or breaker, and also is usually only done when the enclosures are adjacent. Remove the circuit conductors from the old panel. Tie the new service cable back into the utility lines. One guy suggested a 320 amp plug in meter and have 2 200 amp legs going to it. Connect wiring for up to 12 circuits. What do you the pros who chime in suggest.
Check with local electrical inspector to see if the ground wire must also be hooked to water and gas. I have a 200 amp service entrance outdoor breaker box. If relocated, I can only move a short distance to the new box. Full knowledge of the electrical code for wire sizing, placement, height, etc. The ground buss is in direct contact with the metal enclosure. Give us more info for a better guess. This disconnect switch is nothing more than a single breaker box with a 200 amp breaker that i got from home depot for 130 or so dollars as a unit.
If you like your existing 200 amp panel and it has enough spaces 30 or 40 , add a 2nd one and move some circuits over to it. Check that all required grounding is in place and properly fastened. Note you must use anti corrosive grease on all connections in meter can. I'm a carpenter by trade, I only possess basic knowledge for electric. Then, pound two copper ground rods into the ground using a 3-pound sledgehammer. A feasible option could be to install a second breaker panel to feed the increased load; i.
I have had it for over 4 years with no problems and everybody who stays at my house is like whoa that shower kicks out the jams for heat and love it. The process of replacing the equipment that comprises your service is simple and straightforward. Home owner big job Yes but none of the equipment from the 100 amp service can be reused, it will be a total rebuild. They are probably refurbished or seconds or something because anybody whose had had one knows what is up. Before you do any work yourself, on electrical circuits, equipment or appliances, always use a test meter to ensure the circuit is, in fact, de-energized. Make homewyse Better Share this calculator. The other seven are there just to hear the preacher.
As always, if you are in doubt about what to do, the best advice anyone should give you is to call a licensed electrician to advise what work is needed. Because i am installing a disconnect switch outside the house by the meter i can have the panel box inside the middle of the house. They did replace it but the labor to return it after removing it and down time for showers etc. National Electrical Code whichever revision is in use in your locality, check with the office in your city that issues building permits - This is essential to do any electrical work safely and properly, and you're going to want to do that. Your feedback makes this site better for all users. Is a waste of time. Additional considerations and costs The wisest course of action for electrical circuit panel installation is to work with a licensed electrician who can help to accurately determine the precise needs for the home in question.